We have for atleast temporarily disabled the Free Seedbox offer.This was way too often misconstrued as being fully fledged, fully blown and equivalent to a 10-15€ a month service. Which it was not, and it came with exactly 0 guarantees. It was not even based on our own DC or hardware. That 0.20€ payment was often misconstrued as it being fully ... Read More »
Aug 20th 1 server down
1 server remains down from the big chipset cooling issue.
This server has completely failed motherboard and will be replaced soon. Those users will get very hefty SLA compensation.
We are still waiting for more hardware for the enhancements for cooling and eventually the changes will be rolled out on every single server of this model.
Aug 13th 0 servers down
A lot of work remains to be done in regards of the flaky server model, but at this very moment 0 servers are down.We are hoping situation remains so at least until we get more hardware in to apply the fixes.A bunch more of servers got the "janky" 120mm fix today, and the process is now honed in. Takes only roughly 30minutes per server to do when ... Read More »
It has been a mad mad mad week over here at Pulsed Media!One of the server models is having serious issues, this server model we have in large numbers. They are now crashing "left and right" with no obvious reasons, and remote management is extremely flaky on this model; American Megatrends MegaRAC so doing hard reboots and debugging this has been ... Read More »
A single phase on single rack is down. We are investigating.**RESOLVED**Issue was with one of the power distribution modules. These have built-in heat based "fuses" (thermal fuse). PDM being situation very near the server exhaust does not exactly help the case, and significantly derates the rating, so the thermal fuse triggered despite functioning ... Read More »
Coinbase decided to discontinue their merchant tools service, and thus payments via coinbase are not supported anymore as they have shutdown that service.Coinpayments.net is the current recommended gateway, you can use many other cryptos as well than just Bitcoin with them.We do not intend to support Coinbase in future, due to their tactics of ... Read More »
Apr 30th New AC units installed
We have finished installation of several Mitsubishi Heavy Industries AC units into the DC, latest model units with inverters. These units vary the compressor RPM depending upon required load and saves tremendously on energy consumption. Energy efficiency of these very large units are simply incredible.At this very moment as i am writing this, the ... Read More »
Apr 1st M1000 Stock status
Sorry we ran out of stock for the series.
We expect to have more available roughly around Wednesday-Thursday.
In the meantime, check the great Value250 series offers out :)
Helsinki DC is experiencing an outage is 15:54 local time due to a fiber being removed from one of the fiber cross connect rooms.This happened due to 3rd party outdated and incorrect documentation as they were doing maintenance, and thus accidentally removed incorrect unused fibers. A simple human error.This is being fixed right now, ETA should be ... Read More »
There is an outage with number of nodes in Finland DC and we are looking into it.
Expected ETA several hours.
Number of concerned servers is under 20.
UPDATE 12:41: Issue is with power distribution. Power distribution unit or module.
UPDATE 12:46: All nodes affected should be booting now.